Chapter 5: Facilities, Supplies, Equipment, and Environmental Health
5.2 Quality of the Outdoor and Indoor Environment
5.2.5 Fire Warning Systems
220.127.116.11: Smoke Detection Systems and Smoke Alarms
In centers with new installations, a smoke detection system (such as hard-wired system detectors with battery back-up system and control panel) or monitored wireless battery operated detectors that automatically signal an alarm through a central control panel when the battery is low or when the detector is triggered by a hazardous condition should be installed with placement of the smoke detectors in the following areas:
- Each story in front of doors to the stairway;
- Corridors of all floors;
- Lounges and recreation areas;
- Sleeping rooms.
In large and small family child care homes, smoke alarms that receive their operating power from the building electrical system or are of the wireless signal-monitored-alarm system type should be installed. Battery-operated smoke alarms should be permitted provided that the facility demonstrates to the fire inspector that testing, maintenance, and battery replacement programs ensure reliability of power to the smoke alarms and signaling of a monitored alarm when the battery is low and that retrofitting the facility to connect the smoke alarms to the electrical system would be costly and difficult to achieve.
Facilities with smoke alarms that operate using power from the building electrical system should keep a supply of batteries and battery-operated detectors for use during power outages.
RATIONALEBecause of the large number of children at risk in a center, up-to-date smoke detection system technology is needed. Wireless smoke alarm systems that signal and set off a monitored alarm are acceptable. In large and small family child care homes, single-station smoke alarms are acceptable. However, for all new building installations where access to enable necessary wiring is available, smoke alarms should be used that receive their power from the building’s electrical system. These hard-wired detecting systems typically have a battery operated back-up system for times of power outage. The hard-wired and wireless smoke detectors should be interconnected so that occupants receive instantaneous alarms throughout the facility, not just in the room of origin. Single-station batteries are not reliable enough; single-station battery-operated smoke alarms should be accepted only where connecting smoke detectors to existing wiring would be too difficult and expensive as a retrofitted arrangement.
COMMENTSSome state and local building codes specify the installation and maintenance of smoke detectors and fire alarm systems. For specific information, see the NFPA 101: Life Safety Code (1) and the NFPA 72: National Fire Alarm and Signaling Code from the National Fire Protection Association.
The Federal Emergency Management Agency (FEMA) has an online coloring book that can be printed and used to teach children about fire safety at https://www.usfa.dhs.gov/applications/publications/display.cfm?id=208/.
TYPE OF FACILITYCenter, Early Head Start, Head Start, Large Family Child Care Home, Small Family Child Care Home
RELATED STANDARDS18.104.22.168 Compliance with Fire Prevention Code
- National Fire Protection Association (NFPA). 2009. NFPA 101: Life Safety Code. 2009 ed. Quincy, MA: NFPA.